|Maximum Continuous Charge Current (CC Threshold):
|Voltage At End Of Discharge:
|Over Current Protection For Charge:
|105A ± 3A
|Over Voltage Protection:
telecom batteries for solar,
sealed gel batteries
48V 100AH 19”Standard Cabinet Telecom Lithium Ion (LiFePO 4 ) Battery Pack 482.0mm X D 540.0mm X H133.0mm
The 48V Lithium Ion Battery Pack is mainly working as 48VDC backup power source, and it consists of 15 cells of Lithium Iron Phosphate Battery Cells connected in series and telecom specialized high performance and high reliability Battery Management System (BMS). The battery’s +/- output terminals are connected to the +/- terminals of rectifier. When the mains supply is normal, telecom equipment is powered by mains through rectifier and battery pack is also charged through rectifier; When the mains supply is outage, the 48V lithium ion battery pack is supplying power to telecom equipment without any time-delay to ensure telecom equipment is powered without any interruptions, until mains supply resumed or protective power cut-off by BMS due to over-discharge protection activated automatically.
1) Through the host computer to set the protection parameters such as overvoltage, undervoltage, overcurrent, overtemperature, under temperature, short circuit, as well as balance, sleep, capacity, and other functional parameters and various alarm parameters.
2) Supporting monitoring of battery pack related information, battery status information, etc.
3) Supporting storing and exporting related data
4) Supporting writing barcode
5) Remote Control and Telemetering
The management system can be upgraded via the RS485 interface.
Default setting protocol with baud rate 9600, and other protocols are also supported.
After the current limiting module is assembled and enabled by the host computer, the charging current limiting function can be implemented. The current limiting mode is current limiting after charging and overcurrent; the current limiting value is 10 ± 1A.
Battery has Anti-reverse circuit. After the system is powered on, the protection board will be burnt due to the reverse connection of the battery during parallel installation.
The parallel communication function can be realized through the RS485 interface, and it can support up to 6-digit DIP switches (typically 4-digit DIP switches) for setting addresses when communicating in parallel. After parallel connection, the battery pack data can be monitored cyclically through the parallel version of the host computer.
Battery supports no less than 500 battery status data storage functions, protects all data and regular historical data during all state transitions, and stores 1 historical data every hour.
|Standard discharge (1) capacity after standard charge (2)
|Configuration: 15S2P - VHR 3914895LFP-50Ah. Voltage of single cell is 3.2V.
|Voltage at End of Discharge
|Maximum Continuous Charge Current (CC Threshold)
|Over Current Protection for Charge
|105A ± 3A
|Over Voltage Protection
|Over Current Protection for Discharge
|105A ± 3A
|Under Voltage Protection
|Continuous Discharge Power
|Continuous Charge Power
|@ 25 ± 3℃,50%SOC
|@ 25 ± 3℃,80%DOD, 0.2C/0.2C
|Max. 6 month
|Default Setting Value
|(Yes or No)
|Charge Current Limit
|Limited Charge Current Value
|Acceptability range:105 ± 2A
|Method of Charge Current Limit
|Overcharge activates current limit
|Sleep Voltage Set Value
|Acceptability range: 3.3 ± 0.02V
|BMS Power consumption
|Internal Circuit Power Consumption at Mode 1 – Fan is not activated or for natural cooling model with heat radiator
|≤ 40 mA
|Internal circuit power consumption during sleep
|≤ 500 uA
|Balancing Activation Voltage Value
|Balancing Activation Voltage Difference Value
|Full Charge Setting
|Constant voltage value
|54 ± 0.3V
|During constant voltage charging, when the overall voltage is greater than the constant voltage and the current is less than the constant current value, the BMS will assume that the battery capacity is fully charged and the charging MOSFET will be cut off.
|Constant current value
|Interval days of forced recovery charge after overcharge
|In order to ensure the battery capacity, after the battery over-voltage protection, the battery will be forced to resume charging after a fixed time; when the time is configured to 0, this function does not work.
|Under-voltage OFF Time
|Discharge MOS turn-on interval time after undervoltage
|In order to be compatible with the traditional lead-acid charger charging method, the BMS periodically closes the discharge MOSFET for about 7.5 seconds after undervoltage protection, so that the charger detects the battery voltage and turns on the charging. The interval period of the closed discharge MOSFET can be set. When configured to 0, this function does not work.
|Full capacity setting
|Residual capacity setting
RS232 adopts 6Pin straight PCB welding socket (RJ11) to provide RS-232 protocol, the Pin assignment of RJ11 is defined as follow:
S485 adopts 8Pin straight PCB welding socket (RJ45) to provide RS-485 protocol, the pin assignment of RJ45 is defined as follow:
Contact Person: Roy